a:2:{i:0;a:3:{s:5:"title";s:8:"Features";s:2:"id";s:8:"features";s:7:"content";s:1163:"<div id="cont-prod-tab-3" class="prod-desc-field prod-active" style="color: #4a4a4a;">
<ul>
 	<li>Hose rack frame material made of Stainless Steel Gr.304.</li>
 	<li>Provides an immediate water source for fire suppression.</li>
 	<li>Easy individual operation.</li>
 	<li>Max. Service pressure of the Fire Hose Rack Assembly up to 150psi.</li>
 	<li>Hose rack is designed to hold the hose with movable pins for easy &amp; quick operation at the time of Emergency.</li>
 	<li>An automatic release mechanism allows water to flow through the hose after removal of the hose and nozzle.</li>
 	<li>Standard assemblies include:
<ul>
 	<li>Angle Valve or pressure reducing type valve (UL/FM approved)</li>
 	<li>Hose Rack frame material made of stainless steel
<ul>
 	<li>Brush Finish</li>
 	<li>Mirror Finish</li>
 	<li>RED (RAL 3000) Powder Coated Oven Baked</li>
</ul>
</li>
 	<li>Hose rack frame</li>
 	<li>Hose rack nipple</li>
 	<li>Hose coupling</li>
 	<li>Fire Hose - 30 Mtr. (UL Listed)</li>
 	<li>Fog nozzle. (UL approved)</li>
</ul>
</li>
</ul>
</div>
<div id="cont-prod-tab-4" class="prod-desc-field" style="color: #4a4a4a;"></div>";}i:1;a:3:{s:5:"title";s:14:"SPECIFICATIONS";s:2:"id";s:14:"specifications";s:7:"content";s:1454:"<table class="table-striped table-bordered" style="color: #4a4a4a;" border="1">
<tbody>
<tr>
<th>Model</th>
<th>NHR 38V*</th>
<th>NHR 64V</th>
</tr>
<tr>
<th colspan="3">FIRE HOSE</th>
</tr>
<tr>
<td>Fire Hose Type</td>
<td>Single jacket, Light weight
Thermoplastic lining with high tenacity
filament polyester yarn, UL listed</td>
<td>Single jacket, Light weight
Thermoplastic lining with high tenacity
filament polyester yarn, UL listed</td>
</tr>
<tr>
<td>Size &amp; Color</td>
<td>1½" x 30Mtr., White</td>
<td>2½" x 30Mtr., White</td>
</tr>
<tr>
<td>Service Pressure</td>
<td>250 PSI</td>
<td>250 PSI</td>
</tr>
<tr>
<td>Proof Pressure</td>
<td>500 PSI</td>
<td>500 PSI</td>
</tr>
<tr>
<td>Burst Pressure</td>
<td>750 PSI</td>
<td>750 PSI</td>
</tr>
<tr>
<th colspan="3">COUPLINGS</th>
</tr>
<tr>
<td>Type</td>
<td>1-1½" NH Female Threaded Coupling,
Brass</td>
<td>2-½" NH Female Threaded Coupling,
Brass</td>
</tr>
<tr>
<th colspan="3">ANGLE VALVE</th>
</tr>
<tr>
<td>Working Pressure</td>
<td>300 PSI</td>
<td>300 PSI</td>
</tr>
<tr>
<td>Test Pressure</td>
<td>600 PSI</td>
<td>600 PSI</td>
</tr>
<tr>
<th colspan="3">NOZZLE</th>
</tr>
<tr>
<td>Inlet Size</td>
<td>1.5" Female NST Threaded</td>
<td>2.5" Female NST Threaded</td>
</tr>
<tr>
<td>Discharge rate
(in full spray pattern)</td>
<td>130±5GPM @ 100PSI</td>
<td>205±5GPM @ 100PSI</td>
</tr>
</tbody>
</table>";}}